# State what is the significance of conducting phasing out test on a 3-phase transformer? Explain its procedure with a suitable connection diagram.

72 views
State what is the significance of conducting phasing out test on a 3-phase transformer? Explain its procedure with a suitable connection diagram.

Objective: - This test is carried out to identify primary & secondary windings belonging to same phase.

Figure:

Procedure:-  Short primary & secondary winding of other phases expect the one under test. Connect voltmeter to secondary winding. A small DC current is circulated through the primary winding through switch. Now with the help of switch interrupt the DC supply instantly & repeatedly. If voltmeter indicator deflects than it indicates the two windings concerned belong to the same phase. If not deflect then two windings are not belong to same phase. Repeat the procedure by connecting voltmeter to secondary side to next secondary winding till voltmeter gives deflection. In this way we can search the phasing out test.

-Short primary & secondary winding of other phases expect the one under test. -Connect voltmeter to secondary winding. -A small DC current is circulated through the primary winding through switch. -Now with the help of switch interrupt the DC supply instantly & repeatedly. -If voltmeter indicator deflects than it indicates the two windings concerned belong to the same phase. -If not deflect then two windings are not belong to same phase. -Repeat the procedure by connecting voltmeter to secondary side to next secondary winding till voltmeter gives deflection. -In this way we can search the phasing out.

OR

-This test is carried to find out the corresponding HV and LV phase winding. -The circuit diagram is as shown in figure. Here normal ac voltage is applied to one of the HV or LV windings. In this case to HV winding and the voltages across all three LV windings are measured. -The winding across which is much more compared to other two windings represents the secondary of the winding to which supply is connected. -The test repeated for finding out remaining concerned secondary windings in the same manner.

## Related questions

for Delta-Star connection of 3-phase transformer: i) Draw the connection diagram ii) List any two advantages of this connection iii) State its area of application.

What is pressure calibration? State stepwise procedure to test the accuracy of pressure gauge with dead weight tester.

What is energy flow diagram? State its significance from Energy Audit point of view.

Which of the following 3-phase connection of a transformer causes interference with the neighbouring communication lines:  (A) Delta-Star (B) Star-Delta (C) Delta-Delta (D) Star-Star

Explain working of pressure switch with suitable diagram. State the function of differential setting in pressure switch.

What is watchdog timer ? Explain the implementation of time out for ATM with block diagram and program.

State Hall effect. Explain in brief operation of hall effect transducer with its suitable applications.

Explain the principle of ON-OFF control and phase control of AC voltage controller with suitable circuit and waveforms.

What is solenoid valve ? Explain its working with the help of diagram.

Explain with the diagram butt welding. State its applications.

With the help of suitable diagram, explain how humidity is measured with dry and wet bulb thermometer.

Explain the single pass transformer design procedure step by step by giving its flowchart.

Which type of flow is measured by hot wire anemometer and describe its working principle with suitable diagram.

No-load test on a 3-phase induction motor was conducted at different supply voltage and a plot of input power versus voltage was drawn. This curve was extrapolated to intersect the y-axis. The intersection point yields  (A) Core loss (B) Stator copper loss (C) Stray load loss (D) Friction and windage loss

In star-star connection of 3-phase transformer, the triplen harmonics are suppressed by using (A) star connected tertiary windings (B) delta connected tertiary windings (C) neutral conductor (D) additional insulation for the phases

Draw schematic diagram of welding transformer showing constructional features of a welding transformer. Also explain its working.

The transformer connection which has gained considerable popularity to serve 3-phase equipment and single phase lighting load is • Star/Star • Delta/Delta • Delta/Star • Star/Delta

Explain the requirements of elevator motor. State with reason best suitable motor for elevator.

What is the value of form factor in connection with single phase alternating supply systems ? (A) 1.01 (B) 1.11 (C) 1.21 (0) 1.31

The steady-state fault current during a 3 phase terminal fault on a generator is limited by: (1) Transient reactance of the generator (2) Sub-transient reactance of the generator (3) Synchronous reactance of the generator (4) DC off—set during the instant of the fault

A Phase shift transformer is designed to control 150 MVA on a 230 kV, 3 phase line. The phase angle is variable between zero and 15 deg. Calculate the approximate basic power rating of the transformer.  (A) 150 MVA (B) 56 MVA (C) 75 MVA (D) 750 MVA

Explain the leakage flux and its effect with the help of neat diagram.

A large dc motor is required to control the speed of the blower from a 3 -phase ac source. The suitable ac to dc converter is, 3 -phase (a) Fully controlled bridge converter (b) Fully controlled bridge converter with freewheeling diode (c) Half controlled bridge converter (d) Converter pair in sequence control

Draw B-H curve for magnetic material and state its nature. State the significance of hysteresis loop. Also draw the hysteresis loop for hard steel and soft steel.

To protect the power transformer (Y-Y with neutral grounded) against fault, what type of connection do the CTs have ?

Explain memory write ability and storage permanence with suitable diagram.

With the help of neat diagram, explain the construction of current transformer.

The method suitable for heating of a conducting medium is   (a) Induction heating (b) Indirect arc heating (c) Eddy current heating (d) Resistance heating

With neat diagram, explain the working of clip-on ammeter.

Explain the construction of three phase induction motor with neat diagram.

Explain the basic dual slope ADC technique used in digital multimeters with its diagram and measurement cycle.

A capacitor-start single phase induction motor is switched on to supply with its capacitor replaced by an inductor of equivalent reactance value. It will?

The conducting SCR turns-off when the on-state current is (A) below the latching current (B) below the holding current (C) equal to the reverse leakage current (D) zero

Describe procedure for calibration of ammeter with diagram.

A transformer has maximum efficiency at 3/4 full load. The ratio of its iron losses and full load copper loss is : -  a) 16/9 b) 4 / 3 c) 3/4 d) 9 /16

A 3 Phase, 60 Hz generator connected in Y connection, generates a line to line voltage of 23900 V. Calculate the peak line voltage.  (A) 13800 V (B) 33800 V (C) 42300 V (D) 23900 V

a single phase full wave midpoint thyristor converter uses a 230/200V transformer with centre tap on the secondary side. The P.I.V per thyristor is   (A) 100V (B)141.4V (C)200V (D)282.8V

The biggest advantage of T-T connection over the V-V connection of 3-phase power transformation is that it provides.  1.a set of balanced voltages under load 2.a true 3-phase, 4-wire system 3.a higher ratio of utilization 4.more voltages

Describe the importance of three wire and four wire configuration for RTD with suitable circuit diagram.

Which three-phase connection can be used in a transformer to introduce a phase difference of 30o between its output and corresponding input line voltages  (A) Star-Star (B) Star-Delta (C) Delta-Delta (D) Delta-Zigzag

An open-circuit test on a transformer is conducted primarily to measure?

A no-load test is performed on a transformer to determine?